If you use SoftPAC (or PAC Sim for free! for 12-hours at a time), it’s super easy, you’d use the command:
StartOnPulse(On Time (Seconds), On Point)
which takes just those 2 parameters, but handles the under-the-covers configuring of the pulse which the EB2 does itself.
Otherwise, there are ways of setting up similar pulses or “digital events” (AKA event-reactions) via the Mem Map but they’re NOT PRETTY.
As an example… you could have one that’s triggered by the digital ON, delays for X ms, then has the reaction be to turn of that same output. But do you have situations where that output might come on for some other reason (and wouldn’t ALWAYS need to be shut for that X amount of time later)?
Here’s a screen shot of what that would look like, in this case where X = 50 ms and I’m controlling the 1st point on the module that’s not right next to the brain, but the next position over:
Note that once I got it configured and working as I wanted in PAC Manager, I used the “Generic Read/Write” to figure out exactly what I need to write to that address F0D4 0044 which configures a few different pieces of the puzzle…
I hope that helps!