I had a little trouble at first getting the analog modules set up and calibrated too. Are you using PAC Manager or PAC Control to set up your I/O? I think in some situations, the two methods can fight each other. Is the I/O configuration saved to flash so that it loads after a reboot? Support may be able to help if you continue to have trouble with it.